View elegant scenes of light control created with Lutron.
Product specific FAQs
Product specific troubleshooting
Help finding the correct product
Popular tools and resources
Request color samples
Lutron’s NEW facility management tool empowers you to manage your building from anywhere. Easily monitor, control and optimize a Lutron control system from any tablet, PC or smartphone. Each feature is designed around what is most important to you – how well your building is working.
The Specification Guides provide detailed product information to help you specify the right Lutron solution for your project.
Want to learn about installing or programming Lutron solutions? Looking for best practices for selling or specifying? LCI offers online training and in-person workshops for industry professionals.
Visit our Control Center of Excellence for tools and resources to help you select, install, and use LEDs with confidence. Designed for homeowners and industry professionals.
Cannot retrieve the URL specified in the Content Link property. For more assistance, contact your site administrator.
Each type of lighting source (load types) has individual characteristics, which require special types of dimmers. It is important to use a dimmer that is designed, tested, and UL listed for your specific lighting source/load type:
During normal operation, dimmers get warm to the touch. Wallbox dimmer efficiency is typically around 99%. The other 1% is dissipated in the dimmer as heat. So, a 600 W load on a 600 W dimmer would produce around 6 watts of heat. This is approximately the heat generated from a small nightlight. When properly installed per all national and local electrical codes, and when operating on its rated load in a 77º F (25º C) ambient, Lutron dimmer accessible surfaces will stay below the UL limits of 140º F (60º C).
To help the dimmer dissipate the internal heat normal to operation, a typical dimmer is wider than a switch. Dimmers can be ganged together such that the space is the same as switches. A portion of the fins (heat sink) must be removed. The fins are grooved to make the removal of fins easy with a pair of pliers. The removal of fins reduces the wattage capacity (load) the dimmer can control.
The stated VA (volt-ampere) rating is the capacity of the dimmer that includes the magnetic transformer heat losses and the lamp load. A Lutron MLV dimmer UL listed for 1,000 VA can be loaded with a full 1,000 VA lamp load. A transformer dissipates up to 20% of the connected load as heat. Better transformers dissipate less than 10% as heat. Added together, the lamp load and the transformer loss determine the dimmer capacity required.
Electronic low-voltage transformers also dissipate some heat. These inefficiencies are small enough to be accounted for in the dimmer rating. A Lutron ELV dimmer UL listed for 600 W can be loaded with a full 600 W lamp load. If ganged with other dimmers, standard derating rules apply.